Red Phase Control Panels are well equipped with high-tech machineries, qualified personnel having expertise in control panel design, panels manufacturing and development, project planning, testing & commissioning of all types of electrical panels.
A Electrical distribution Panel board is a component of an electricity supply system which divides an electrical power feed into subsidiary circuits, while providing a protective fuse or circuit breaker for each circuit in a common enclosure.
Our Wide Range of Distribution Panels:–
1. Outdoor Feeder Panel
Low-voltage feeder pillars form a basic part of most public and many private distribution networks. Feeder pillars are connected to the distribution board. These pillars are usually made of strong and weather proof materials like Galvanized sheet steel, stainless steel. Feeder pillars are mainly used in electrical installations.
2. Distribution Panel with Power Factor Controller
Automatic Power Factor Control Panel to achieve unity/near unity power factor. The power factor controller of our APFC Panels monitors the reactive power which intern helps in saving energy.
3. AMF Control Panels
AMF panel are designed to provide emergency power during a mains supply failure. During operation, the control panel of the AMF monitors the mains entering the building. If a mains failure occurs, the panel will disconnect the mains from the load, the generator is started and its output connected to the load (which is the appliances, lights, etc in use within the factory/office/house at the time of mains failure). The generator continues to supply the building until the mains supply returns. The generator then automatically disconnects, stops and the mains is re-connected to the load.
The AMF panel reverts to the standby mode ready to respond in the event of another mains failure. With the generator in ‘Auto’ mode, the incoming main is monitored continuously. If the mains voltage falls outside the preset limits, a ‘mains failure’ has occurred and the process of starting the generator set is initiated.